Rugged, and designed for heavy-duty use, POWERSTAT® Variable Transformers provide excellent power regulation with negligible variation in output voltage from no-load to full-load current. They provide a simple, rugged method of controlling electrical voltage, current and power. They take in utility line voltage and provide continuously adjustable output voltage. Available in both manual and motor-driven options, they offer high current ratings, long life, superior overload capacity and exception resistance to contaminants such as fungus and salt spray.

The 10C Series are offered in single and three phase manually operated assemblies. The 10C Series units operate from 120V lines 10C Series units are rated at 2.25A for constant current loads. All types are open construction designed for back-of-panel mounting. The tapping arrangement permits an output voltage of 0 to line voltage or 10% above line voltage. All models can be operated at any frequency between 50 and 2000 Hz without reduction in allowable output current.

The 1156D Series are offered in single and three phase assemblies. The 1156D Series types operated from 120V lines. The rated output for constant current loads is 50A. The load rating ranges from 50A-450A depending on input voltage. Please refer to the catalog rating charts. The 1156D Series can be operated at any frequency between 50 and 500 Hz. Refer to Figure A in our catalog for the allowable output current at the higher rated frequency. 1156D Series may be bench or back-of-panel mounted. Available in open construction, screened, terminal enclosure and screens or with a NEMA 1 Enclosure. Units are can be operated manually or motor-driven. The 1156D Series assemblies are completely self-contained. They are fully assembled and include all paralleling chokes and connections, input and output terminals for copper wire, bases, shafts, lifting eyes and output fuses.

The 116C Series operate from 120V lines. The rated output for constant current loads is 10A. Single, manually operated units have both 3-hole and 4-hole mounting arrangements; all others have a 4-hole mounting. The 116C Series can be operated at any frequency between 50 to 1500 Hz without reduction in allowable output current. Available in open construction, coil & terminal enclosure or with cord-plug/receptacle sets. Except for the cord-plug/receptacle sets the units are available as manual or motor-driven.

The 117C Series operate from 120V lines. The rated output for constant current loads is 12A. Single, manually operated units have both 3-hole and 4-hole mounting arrangements; all others have a 4-hole mounting. The 117C Series can be operated at any frequency between 60 to 1500 Hz without reduction in allowable output current. Available in open construction, coil & terminal enclosure or with cord-plug/receptacle sets. Except for the cord-plug/receptacle sets the units are available as manual or motor-driven.

The 1256D Series are offered in single and three phase assemblies. The 1256D Series types operated from 240V lines. The rated output for constant current loads is 28A. The load rating ranges from 28A-252A depending on input voltage. Please refer to the catalog rating charts. The 1256D Series can be operated at any frequency between 50 and 500 Hz. Refer to Figure A in the catalog for the reduction in allowable output current when operated at higher than rated frequency. The 1256D Series may be bench or back-of-panel mounted. Available in open construction, screened, terminal enclosure and screens or with a NEMA 1 Enclosure. Units are can be operated manually or motor-driven. The 1256D Series assemblies are completely self-contained. They are fully assembled and include all paralleling chokes and connections, input and output terminals for copper wire, bases, shafts, lifting eyes and output fuses.

The 126 Series are offered in single and three phase assemblies. The 126 Series types operated from 120V lines. The rated output for constant current loads is 15A. The 126 Series can be operated at any frequency between 50 and 2000 Hz. Refer to Figure A in our catalog for the allowable output current at the higher rated frequency. Available in open construction, coil & terminal enclosure or with cord-plug/receptacle sets. Except for the cord-plug/receptacle sets the units are available as manual or motor-driven.

The 1296D Series are offered in single and three phase assemblies. The 1296D Series types operated from 240V lines. The rated output for constant current loads is 35A. The load rating ranges from 35A-350A depending on input voltage. Please refer to the catalog rating charts. 1296D Series may be bench or back-of-panel mounted. Available in open construction, screened, terminal enclosure and screens or with a NEMA 1 Enclosure. Units are can be operated manually or motor-driven. The 1296D Series assemblies are completely self-contained. They are fully assembled and include all paralleling chokes and connections, input and output terminals for copper wire, bases, shafts, lifting eyes and output fuses.

The 12C Series are offered in single and three phase manually operated assemblies and operate from 240V lines. The 12C Series units are rated at 0.7A for constant current loads. All types are open construction designed for back-of-panel mounting. The tapping arrangement permits an output voltage of 0 to line voltage or 10% above line voltage. All models can be operated at any frequency between 50 and 2000 Hz without reduction in allowable output current.

The 136B Series are offered in single and three phase assemblies. The 136B Series types operated from 120V lines. The rated output for constant current loads is 22A. The 136B Series can be operated at any frequency between 50 and 2000 Hz. Refer to Figure A in our catalog for the allowable output current at the higher rated frequency. Available in open construction, coil & terminal enclosure or with cord-plug/receptacle sets. Except for the cord-plug/receptacle sets the units are available as manual or motor-driven.

The 146 Series are offered in single and three phase assemblies. The 146 Series types operated from 120V lines. The rated output for constant current loads is 30A. The 146 Series can be operated at any frequency between 50 and 550 Hz. Refer to Figure A in our catalog for the allowable output current at the higher rated frequency. Available in open construction or coil & terminal enclosure. Manual or motor-driven.

The 21 Series are of open construction and primarily designed for back-of-panel mounting. The rated output for the Type 21 Series is 5A for constant current loads. The 21 Series types operate from 120V lines. The tapping arrangement permits an output voltage range of zero to line voltage or zero to 17% above line voltage. The 21 Series can be operated at any frequency between 50 and 2000 Hz without reduction in allowable output current. Manual or motor-driven operated units are available.

The 216C Series operate from 240V lines. The rated output for constant current loads is 3.5A. Single, manually operated units have both 3-hole and 4-hole mounting arrangements; all others have a 4-hole mounting. The 216C Series can be operated at any frequency between 50 to 1500 Hz without reduction in allowable output current. Available in open construction, coil & terminal enclosure or with cord-plug/receptacle sets. Except for the cord-plug/receptacle sets the units are available as manual or motor-driven.

The 217C Series operate from 240V lines. The rated output for constant current loads is 5A. Single, manually operated units have both 3-hole and 4-hole mounting arrangements; all others have a 4-hole mounting. The 116C Series can be operated at any frequency between 60 to 1500 Hz without reduction in allowable output current. Available in open construction, coil & terminal enclosure or with cord-plug/receptacle sets. Except for the cord-plug/receptacle sets the units are available as manual or motor-driven.

The 22 Series are of open construction and primarily designed for back-of-panel mounting. The rated output for the Type 22 Series is 2.25A for constant current loads. The 22 Series types operate from 240V lines. The tapping arrangement permits an output voltage range of zero to line voltage or zero to 17% above line voltage. The 22 Series can be operated at any frequency between 50 and 2000 Hz without reduction in allowable output current. Manual or motor-driven operated units are available.

The 226 Series are offered in single and three phase assemblies. The 226 Series types operated from 240V lines. The rated output for constant current loads is 7.5A. The 226 Series can be operated at any frequency between 50 and 2000 Hz. Refer to Figure A in our catalog for the allowable output current at the higher rated frequency. Available in open construction, coil & terminal enclosure or with cord-plug/receptacle sets. Except for the cord-plug/receptacle sets the units are available as manual or motor-driven.

The 236B Series are offered in single and three phase assemblies. The 236B Series types operated from 240V lines. The rated output for constant current loads is 10A. The 236B Series can be operated at any frequency between 50 and 2000 Hz. Refer to Figure A in our catalog for the allowable output current at the higher rated frequency. Available in open construction, coil & terminal enclosure or with cord-plug/receptacle sets. Except for the cord-plug/receptacle sets the units are available as manual or motor-driven.

The 246 Series are offered in single and three phase assemblies. The 246 Series types operated from 240V lines. The rated output for constant current loads is 15A. The 246 Series can be operated at any frequency between 50 and 550 Hz. Refer to Figure A in our catalog for the allowable output current at the higher rated frequency. Available in open construction or coil & terminal enclosure. Manual or motor-driven.

The POWESTAT® Full Range Regulator Controller is a solid-state sensing device which monitors and detects any variation in load voltage or current and operates a POWERSTAT® Variable Transformer synchronous drive motor to correct the variation and hold the output constant at a selected value.

The Enclosed L Series are specially designed to minimuze the possiblity of shock hazard. For maximum protection and safety, all models are equipped with a grounded NEMA cord-plug assembly, on-off switch, pilot light, output receptacle and fuse. All models are designed for 120V single phase service. The L Series have slots at the rear that accept wall hanger brackets.

L2M Series are 120V, Single Phase. You have a choice of 0-140V or 0-280V output. Easy-to-read Output Voltage and Current Meters. NEMA Style Receptacle and 5-WAY Binding Post Output Connections. Rocker Style "On Indicating" Thermal Magnetic Circuit Breaker. Portable and compact design.

The Q116U Series operates from 120V lines. The rated output for constant current loads is 9A. The Q116U Series can be operated at any frequency between 50 to 1500 Hz without reduction in allowable output current. Open construction, manually operated.

The Q117U Series operates from 120V lines. The rated output for constant current loads is 10A. The Q117U Series can be operated at any frequency between 60 to 1500 Hz without reduction in allowable output current. Open construction, manually operated.

The Q216U Series operates from 240V lines. The rated output for constant current loads is 3.5A. The Q216U Series can be operated at any frequency between 50 to 1500 Hz without reduction in allowable output current. Open construction, manually operated.

The Q217U Series operates from 240V lines. The rated output for constant current loads is 5A. The Q217U Series can be operated at any frequency between 60 to 1500 Hz without reduction in allowable output current. Open construction, manually operated.